I went to replace a light fixture and found a 3 way switch wired in a way I have never heard of. Both switches had power coming into the switch box. Then the wire going to the light fixture had only the hot wire connected, white was not connected to anything. Crappy electrical drawing
Can someone explain what is going on and the best way to fix it? The wires going to the light fixture are 2 wire plus ground. Not the 3 wire plus ground I am used to seeing.